VIETNAM STANDARD - TCVN 7336: 2003
- Fire protection
- Automatic sprinkler system
- Design and installation requirements
Fire protection - Automatic sprinkler systems - Design and installation requirements
TCVN 7336: 2003 compiled by Technical Committee, TCVN / TC on Fire Prevention and Fighting, General Department
Proposed Quality Measurement Standards issued by the Ministry of Science and Technology.
1. SCOPE OF APPLICATION
This International Standard specifies requirements for the design and installation of self-extinguishing sprinkler systems
water, foam (hereinafter referred to as sprinkler system) in buildings and construction works
new or renovated.
This International Standard also applies to sprinkler-controlled, bc-head flood extinguishing systems
and remote control or manual.
This standard does not apply to extinguishing systems for:
- Buildings with special functions and technological equipment outside of those buildings;
- Underground underground chambers of the mining industry;
- Petroleum tank.
2. EXCLUSIVE STANDARDS
TCVN 4756: 89, Rules for earthing and air connection of electrical equipment.
TCVN 5738: 2001, Automatic fire alarm system - Technical requirements.
TCVN 6305-1: 1997 (ISO 6182-1: 1993) Fire prevention and fighting - Automatic sprinkler system -
Part 1: Requirements and testing methods for sprinklers.
TCVN 6305-2: 1997 (ISO 6182-2: 1993) Fire prevention and fighting - Automatic sprinkler system -
Part 2: Requirements and testing method for wet type alarm valve, brake saddle and alarm mechanism
TCVN 6305-3: 1997 (ISO 6182-3: 1993) Fire prevention and fighting - Automatic sprinkler system -
Part 3: Requirements and testing method for dry pipe valves.
TCVN 6305-4: 1997 (ISO 6182-4: 1993) Fire prevention and fighting - Automatic sprinkler system -
Part 4: Requirements and test methods for fast valve opening mechanism.
TCVN 6305-5: 1997 (ISO 6182-5: 1993) Fire prevention and fighting - Automatic sprinkler system -
Part 5: Requirements and testing methods for overflow valves.
3. TERMS AND DEFINITIONS
This International Standard uses the terms and definitions given in TCVN 6305: 1997.
4. GENERAL PROVISIONS
4.1. Fire extinguishing systems designed in accordance with this standard shall have manual control.
4.2. Sprinkler systems shall be designed so that they can both function
fire fighting at the same time with automatic fire alarm function.
4.3. Sprinkler systems must be designed on the basis of the required production line technology
economic and technical criteria.
Download Standards to install sprinkler system: https://secufiles.com/folder/3837/Tieu_Chuan_Lap_Dat_He_Thong_Sprinkler